Indoor fire extinguishing deviceCharacteristics:
The device operability is provided at an operating hydrostatic pressure of 0.1 to 0.6 MPa.
Weight with accessories should be no more than 2.5 kg.
Overall dimensions of UVP should be no more than 300x300x50 mm.
Sleeve length can be (10, 15, 20) + – 0.1 m.
Manufactured according to technical specifications TU BY 100144393.018-2006.
The device meets the requirements of building codes of the Republic of Belarus SNB 4.01.02-03 “Fire-fighting water supply”.To order
Internal fire extinguishing device is designed to extinguish fires at an early stage in buildings of classes F1.3 and F1.4 for functional fire hazard according to SNB 2.02.01-98 “Fire-technical classification of buildings, building structures and materials” …
The device can be placed in a container bag made of fabric or in a metal cabinet, it is connected to the tap on the branch of the drinking water supply in the apartment after the metering device for the amount and flow of water in any place convenient for its installation: in the bathroom, sanitary unit , kitchen, hallway.
Recommended servicesSee all services
Installation of external networks and power supply lines, arrangement of internal power supply networks